Do you know the installation and maintenance of acid mist scrubber?
1. The user shall carry out concrete foundation construction according to the foundation material drawing provided by our company. The device surface of the root bottom shall be guaranteed to be on the same horizontal surface, and the bottom foot of the acid mist washing tower shall be fixed on the steel plate at the root bottom with bolts or taps.
2. When the fan is installed, the sundries shall be prevented from falling into the fan. After the completion of acid mist scrubber, it is necessary to remove the dirt in the tower before commissioning.
3. Since FRP products are usually inflammable, it is forbidden to use open fire in the process of device and repair.
4. If the fan is installed indoors, it is necessary to adopt rainproof measures for the motor of the fan.
5. It is necessary to assign a special person to handle the acid mist scrubber, often check whether the fan can work normally, whether the liquid level can be normal or not, whether the float switch in the liquid level tank can be normal, whether the solution concentration can be in the regular scale, etc. if any problem is found, it should be dealt with in time.
6. In order to ensure the liquid level in the liquid storage tank and avoid the rise and fall of the liquid level when the fan is switched on and off, it is necessary to open the floating ball water supply valve after the fan is turned on, and close the floating ball water supply valve before the fan is closed. The height of liquid level should be controlled about 650mm above the ground statically.
7. The metal support of acid mist scrubber shall be subject to anti-corrosion treatment at least twice a year
酸雾净化塔操作规程 | 酸雾净化塔的工作原理
Code of operation for acid mist purification tower working principle of acid mist purification tower
1. The acid mist scrubber should be installed on the concrete foundation 100mm above the ground, and the water pump and fan should be used as the concrete foundation separately as required.
2. Pay attention to protection during transportation and installation, and do not damage the body and components.
3. When the absorption tower is delivered from the factory, the factory will transport it in sections according to the specific conditions, and send personnel to the site for installation and commissioning.
4. If the absorption tower is installed and operated outdoors, pay attention to antifreeze at the bottom pool in winter.
What are the remarkable characteristics of acid mist purification tower
5. The water tank at the bottom of the absorption tower is provided with a liquid level mark, and the absorption liquid must be filled according to the liquid level mark before use. Pay attention to supplement the absorption liquid during use.
6. The circulating water pump shall be turned on for 2-3 minutes before the blower is turned on. When the blower is turned off, the blower shall be turned off for 1-2 minutes before the circulating water pump is turned off.
7. The acid concentration of the liquid in the tank at the bottom of the tower and the purification degree of the gas at the outlet shall be checked regularly according to the service conditions. If it exceeds the standard, the absorption liquid in the tank at the bottom shall be replaced.
8. The absorption tower shall be overhauled once a year and a half to two years, and the filling condition of disc spray pipe and packing shall be checked and cleaned.